Posted 5/5/2019 19:06 (#7478108 - in reply to #7466212) Subject: RE: New gas range
You can do a shut in test with the gas meter. If your furnace and dryer do not have standing pilot lights you can simply mark the test dials on your gas meter. Test dials should be bottom dials and marked 1/4 or 1/2 ft dials. Mark them with a sharpie and give it a half hour. If they don’t move your good.
If your furnace or dryer do have standing pilots just valve them off at the appliance.